Series 641RM Air Velocity Transmitter with Remote Probe
For Remotely Mounting Electronic Enclosure
The Series 641RM Air Velocity Transmitter with Remote Probe features the same highly accurate heated mass flow sensor as the Series 641, with a remote probe construction. The units 6´ cable which connects the sensing probe with the electronic enclosure allows the enclosure to be mounted where it can be more easily accessed.
NIST CALIBRATION available in Product Configurator.
- Exhaust stack flow monitoring
- Air control in drying processes
- HVAC air velocity measurements
- Fan supply and exhaust tracking
- Clean room ventilation monitoring
Models & Ordering
- Clean air and compatible, non-combustible gases.
- 3% FS Process gas: 32 to 122°F (0 to 50°C); 4% FS Process gas: -40 to 32°F & 122 to 212°F (-40 to 0°C & 50 to 100°C).
- 250 FPM (1.25 MPS) to 15,000 FPM (75 MPS).
- Response Time:
- Flow: 1.5 s to 95% of final value (output filter set to min.).
- Temperature Limits:
- Process: -40 to 212°F (-40 to 100°C). Ambient: 32 to 140°F (0 to 60°C).
- Pressure Limit:
- 100 psi (6.89 bar) maximum.
- Humidity Limit:
- Power Requirements:
- 12 to 35 VDC, 10 to 16 VAC. 1.5 A rating required on supply due to initial power surge drawn by transmitter.
- Output Signal:
- 4 to 20 mA, isolated 24 V source, 3 or 4-wire connection.
- Output Filter:
- Selectable 0.5-15 s.
- Loop Resistance:
- 600 Ω max.
- Current Consumption:
- 300 mA max.
- Electrical Connections:
- Screw terminal.
- Mounting Orientation:
- Unit not position sensitive. Probe must be aligned with airflow.
- 13.2 oz (374.26 g).
- Cable Length:
- 6' (1.82 m).
- Probe Length:
- 12" (30.48 cm) standard.
- Probe Diameter:
- 5/16" (0.79 cm).
- OPTIONAL DISPLAY VERSION
- 4-1/2 digit 1/2" red LED.
- 1 FPM, 0.01 MPS (10 FPM @ 10,000 and 15,000 FPM ranges).
- 13.9 oz (394.16 g).
- Output signal conditioning with digital filtering
- Install in tight spaces with compact design
- Easy setup with on-board buttons
|Model Number||Description||Usually Ships*||Price||Order|
|A-156||Flange mounting plate with 1/2" female NPT.||Same Day||$19.00||Order|
|A-158||Split flange.||Same Day||$16.50||Order|
|A-159||Mounting gland with 1/2" male NPT.||Same Day||$32.75||Order|
|641-LED||Field-upgradeable LED.||1-2 Weeks||$157.00||Order|
Series 641RM Air Velocity Transmitter, 6" probe, with LED display.
Air Velocity Transmitter
|3 ft. Cable Length
10 ft. Cable Length
15 ft. Cable Length
20 ft. Cable Length
25 ft. Cable Length
30 ft. Cable Length
NIST Certificate of Calibration
Stainless Steel Tag
- We have recently replaced a Dwyer air velocity transmitter (PFS1300204) with a Dwyer Series 641. The new sensor works fine for only a few days and then starts reading almost no flow. These devices are used in an Air Scrubber application (exhaust stack). Is this the right application for the Series 641? I suspect that moisture might be the issue, but I cannot confirm.
- I do not think you are using the 641 series air velocity transmitter in an appropriate application. Any moisture or particulates in the exhaust could be causing damage to the hot wire sensor, leading to the failure. The difference in the sensors is probably why you got longer life out of the PFS series, which unfortunately, is no longer available. The PFS series used a glass filled polyester sensor, which is a little more robust and can with stand the elements a little better. In your specific application, you might take a look at our 641B series which uses a heated mass flow sensor which can be used in dirty air environments.
Photo DownloadsYou must be logged in to view this content.
Click here to login to your account.